The Data Center Optimization Initiative (DCOI) was established in the Office of Management and Budget (OMB) memorandum M-16-19 dated August 1, 2016. DCOI supersedes the Federal Data Center Consolidation Initiative (FDCCI) and fulfills the data center requirements of the Federal Information Technology Acquisition Reform Act (FITARA).
DCOI requires federal agencies to develop and report on data center strategies to consolidate inefficient infrastructure, optimize existing facilities, improve security posture, achieve cost savings, and transition to more efficient infrastructure, such as cloud services and inter-agency shared services.
General Services Administration (GSA) Office of Government-wide Policy (OGP) is the managing partner of the Federal Government’s data center line of business and data center shared services. A DCOI Community of Practice (CoP) has also been formed (see links below).
DEFINITION OF A DATA CENTER AND TIERED VS. NON-TIERED
DCOI defines a data center as having 1 or more servers and defines “tiered” data centers (which is to replace the previous “core” data center concept) as having all of:
- A separate physical space for IT infrastructure
- An uninterruptible power supply (UPS)
- A dedicated cooling system or zone
- A backup power generator
Tiered data centers are required to have plans for cost savings and track and report progress on those plans. Non-tiered data centers are to be phased out.
METRICS REQUIRED FOR TIERED DATA CENTERS
|METRIC||CALCULATION||TARGET (by the end of FY2018)|
|Energy metering||% of total gross floor area in the tiered inventory located in tiered data centers with power metering||100%|
|Power usage effectiveness (PUE)||Total energy used/Total IT equipment energy used||
<=1.5 for existing data centers
<=1.4 for new
|Virtualization (HPC nodes excluded from this metric)||(Total server count + Total virtual OS)/Total physical servers||>=4|
|Server utilization and automated monitoring (HPC nodes excluded from this metric)||Average server utilization x Percent of DCs Fully Equipped with Automated Monitoring||>=65%|
|Facility utilization||(Total active rack count x 30 sf)/Total Gross Floor Area||>=80%|
DATA CENTER ENERGY PRACTITIONER (DCEP)
DCOI states that all tiered data centers shall have at least one certified DCEP assigned to manage data center performance and continued optimization. Information on the DCEP training program is available here.
A contact form for questions and/or to request more comprehensive Center of Expertise support for DCOI implementation in federal data centers is available here.
Please see the links below for other helpful information and guidance related to DCOI.