Reach us with questions or suggestions, or subscribe to our Quarterly Data Center Energy Practitioner (DCEP) newsletter at firstname.lastname@example.org
Ask the Experts!
Our answers to incoming questions from the CoE community!
Q: I have been reviewing the PUE calculator on your website. I’m currently working with a client and we are in the very early stages in a project. The client is looking for PUE and this stage, the best we can do is provide a PUE estimate using a tool like the one on your website. I have a question regarding the inputs. We are looking to go with 70 degree entering chilled water into the cooling coils. The chilled water entering temperature in the PUE estimator appears to only go up to 55 deg F. Is there any way to increase this about to 70 deg F? Please advise.
Q: Can you point us to any documentation on what sorts of requirements we should be asking for in terms of selecting the exact transformer to use? This application will be single-sourced HPC systems, so we'll expect fairly high loading on the transformer most of the time. We need to understand the characteristics/attributes that we want and find them in a USA supplier or justify why we need them and that no USA supplier offers them. Thanks for any pointers you may have.
A: The DOE 2016 requirement for low-voltage distribution transformer efficiency is specified at 35% load, which is probably a good assumption for a commercial building, but a bad one for a data center striving to make the best use of limited power distribution resources. That standard requires no less than 98.83% efficiency (again, at 35% load). Overall transformer losses are the total of a fixed no-load loss and a load loss that scales with the square of the load, thus the DOE standard numbers are dominated by the no-load loss and the high loads that you are striving for will be dominated by the load loss and there are trade-offs in transformer design between the two.
I'd suggest getting the efficiency curve from Powersmiths for their ESAVER-50H (optimized for high loading) and use that to specify the efficiency requirement at e.g. 75% load, which is a standard rating point. Other parameters, especially impedance, need to be managed to optimize inrush current, fault level, and arc-flash to make sure it will integrate with the existing installation. We learned this the hard way at FLEXLAB. Hope this helps!
Q: A quick question about CRAH VFD fan control. At some WHS data centers, there are some CRAH units with VFDs controlling to an underfloor static pressure setpoint of 0.1" wc. The static pressure in the room varies from 0.02" to 0.04" wc, so the VFDs are always running at 100% trying to reach the setpoint. I am planning to propose controlling the VFDs to cold aisle temperature setpoints instead of the UF static pressure setpoints. The goal would be to reduce CRAC VFD fan speed. In you experience, do you think this is the right approach?
A: Your approach to CRAH fan control should work well in your application, given that with your cold-aisle isolation and blanking panels, you should have good air management. So the chilled water valves in the CRAHs would be controlled on supply air temperature (correct?), and the fans would be controlled on cold-aisle temperature; we recommend using a sample of the top-of-rack temperatures for control, and monitoring the rest of the inlet temperature sensors to alarm any hot spots. This scheme is a relatively direct way to ensure that the IT equipment is getting the recommended inlet air temperature. Even better than rack inlet temperatures, is to get the inlet temperatures directly from the IT equipment, but often this access is made difficult by security protocols.
Q: How do systems that are outside air economizers with evaporative cooling work?
A: Increasingly indirect economizer/evaporative cooling schemes available. These are air-handling units outside the data center that use air-to-air heat exchangers and indirect evaporative cooling, usually with a compressor-based backup. Ducts connect these AHUs to the hot and cold air plenums in the data centers. All provide most of the energy savings of an air-side economizer without the (overblown, in most cases) concern about bringing outside air into the data center. And they are likely to be a system with a higher capital cost than a conventional ASE.